|For Your Home|
|When to Turn Off Your Lights|
The cost effectiveness of when to turn off lights depends on the type of lights and the price of electricity. The type of light is important for several reasons. All types of lights have a nominal or rated operating life, which is the total number of hours that they will provide a specified level or amount of light. However, the operating life of all types of light bulbs is affected by how many times they are turned on and off. The more often they are switched on and off, the lower their operating life. The exact number of hours that switching lights on and off reduces the total operating life depends on the type of light and how many times it is switched on and off.
Fluorescent lights are more expensive to buy, and their operating life is more affected by the number of times they are switched on and off, relative to incandescent lights. Therefore, it is a cost trade-off between saving energy and money by turning a light off "frequently" and having to replace the bulbs "more" frequently. This is because the reduction in usable lamp life due to frequent on/off switching will probably be greater than the benefit of extending the useful life of the bulb from reduced use. By frequent we mean turning the light off and on many times during the day.
It is a popularly held belief that fluorescent lights use a "lot" of energy to get started, and thus it is better not to turn them off for "short" periods. There is an increase in power demand when a light is switched on, and the exact amount of this increase depends on the type of ballast and lamp. The ballast provides an initial high voltage for starting the lamp and regulates the lamp current during operation. There are three basic types of ballasts: magnetic (of which there are energy-efficient and not so energy-efficient types), cathode-disconnect, and electronic. All types can operate two or more lamps simultaneously. There are three main methods that are used in a lamp's ballast to start the lamp: preheat, rapid-start, and instant-start.
In any case, the relatively higher "inrush" current required lasts for half a cycle, or 1/120th of a second. The amount of electricity consumed to supply the inrush current is equal to a few seconds or less of normal light operation. Turning off fluorescent lights for more than 5 seconds will save more energy than will be consumed in turning them back on again. Therefore, the real issue is the value of the electricity saved by turning the light off relative to the cost of relamping a fixture. This in turn determines the shortest cost-effective period for turning off a fluorescent light.
The value of the energy saved by turning a fluorescent light (or array of lights) off depends on several factors. The price an electric utility charges its customers depends on the customer "classes," which are typically residential, commercial, and industrial. There can be different rate schedules within each class. Some utilities may charge different rates for electricity consumption during different times of the day. It generally costs more for utilities to generate power during certain periods of high demand or consumption, called peaks. Some utilities can charge commercial and industrial customers more per kilowatt-hour (kWh) during peak periods than for consumption off-peak. Some utilities may also charge a base rate for a certain level of consumption and higher rates for increasing blocks of consumption. Often a utility adds miscellaneous service charges, a base charge, and/or taxes per billing period that could be averaged per kWh consumed, if these are not already factored into the rate.
Then you need to find out what you are paying for electricity per kWh (in general and during peak periods). You will need to look over your electricity bills and see what the utility charges per kWh. Multiply the rate per kWh by the amount of electricity saved, and this will give you the value of the savings. Continuing with the example above, let us say that your electric rate is 10 cents per kWh. The value of the energy savings would then be 0.4 cents ($ 0.004). The value of the savings will increase the higher the watt rating of the bulb, the greater the number of bulbs controlled by a single switch, and the higher the rate per kWh.
The most cost-effective length of time that a light (or array of lights) can be turned off before the value of the savings exceeds the cost of having to replace bulbs (due to their shortened operating life) will depend on the type and model of bulb and ballast. The cost of replacing a bulb (or ballast) depends on the cost of the bulb and the cost of labor to do it.
Lighting manufacturers should be able to supply information on the duty cycle of their products. In general, the more energy-efficient a bulb/light is, the longer you can keep a light on before it is cost effective to turn it off.
Email Us for more energy efficiency information to speak with an Energy Advisor call, 1-800-562-1482.
Source: Energy Efficiency and Renewable Energy (EERE), Department of Energy
|Copyright © Aclara Technologies LLC. All Rights Reserved.|